If your heating is on a lot of the time assuming your house is insulated well ,your radiators are sized correctly. you could try start with as low...
It will be also down to where the pump is in relation to the feed and vent . Locate the feed and vent and run a magnet over it , if its blocked...
Erm , let me think on this
Lol , its ****ing it down and freezing mate , ( slight exaggeration on the freezing )
On an old system the feed pipe , expansion pipe and pump will be all over the place , all 3 want "close coupling " .
You may need a plumber in ,.
DIY gone mad if you ask me lol
As above with Shaun , you will never match the unit and pan 100% even if you get it close, the unit will change colour over the years especially...
Yep I have noticed the "log -in pain" but no big problem here
Not sure what you mean , you wont find a pan at 350 , but will find a WC unit of roughly 350 mm
Yes it shouldnt be there , just take the wheel off , no dramas
No matter what you do , its going to have to be repaired properly one day
You know me so well , yep will be looking for a bar tomorrow night for the Town v West Ham match
You used to buy some a rubber attachment shower thing from woolworths a million years ago , bloody garbage.
A decent mixer tap with shower...
Sat in a hotel in Folkestone , getting tunnel in the morning , driving to Spain stop off somewhere in France tomorrow night , 5 nights in Spain...
Separate names with a comma.